Hungry rat blamed for Fukushima blackout
Alleged culprit. The dead rat found inside a temporary electric switchboard. Operators of the Fukushima plant claim it caused cooling systems to shut down.
TOKYO: The operator of the crippled Fukushima Daiichi nuclear plant says it has found what it believes is the cause of an extended blackout that disabled vital cooling systems earlier this week: the charred body of a rat.
The operator, Tokyo Electric Power, said when its engineers looked inside a faulty switchboard, they found burn marks and the rodent's scorched body. The company said it appeared the rat had somehow short-circuited the switchboard, possibly by gnawing on cables.
TEPCO has blamed problems with the switchboard for the power failure that began on Monday, cutting off the flow of cooling water to four pools used to store more than 8800 nuclear fuel rods. It took TEPCO almost a day to restore cooling to the first of the affected pools, with cooling of the final pool resuming early on Wednesday.
TEPCO said it would have taken several days for temperatures in the pools to have risen above the safe level of 65 degrees. Still, the blackout served as an uncomfortable reminder to many Japanese about the continuing vulnerability of the plant, which suffered a triple meltdown in March 2011 after a huge earthquake and tsunami knocked out cooling systems. It was the worst nuclear disaster since Chernobyl.
Two years later, the Fukushima plant still relies on makeshift cooling systems, some of which were built as stopgap measures in the frantic weeks after the accident. The spent fuel pools have been a particular source of concern because they contain much more radioactive material than the three reactor cores that melted down two years ago, forcing the evacuation of 160,000 people.
A TEPCO spokesman, Masayuki Ono, said temperatures in the pools were cooling, though it would take several days for them to get back to their pre-blackout levels.
New York Times